How often should an AOV be tested?
AOV systems need to be tested both weekly and monthly. Weekly tests of your smoke control system should be carried out to check the operation of the system. During the monthly test, the failure of the primary power supply should be simulated, and a check made that the system has automatically switched over to the secondary power supply.
Our Testing & Maintenance page gives further information as well as our free smoke control testing and maintenance log sheet.